The scope of use of explosion proof led lighting is now more and more extensive, so many companies are replacing them in batches. This type of lighting device is better than ordinary lighting devices, and it is not prone to problems, and the cycle of use is longer. The most important thing is that safety is several times that of ordinary lighting equipment. With these advantages, it is naturally more acceptable to enterprises, but after purchasing explosion proof lighting equipment, how to properly and effectively install the explosion-proof lamps has become a headache for many companies, especially small enterprises.
Because it was replaced for the first time, and the quantity is relatively small, I wanted to replace it with the electrician of the company after purchasing it. However, it was found that it is difficult to replace the explosion-proof lamp, and I don’t know how to operate it. The problem is naturally to make the enterprise more troubled, then how should we operate?
If you don’t know how to install the explosion proof led flood lighting correctly and effectively, then it doesn’t matter, because the explosion-proof lamp can be directly mounted on the wall through the fasteners, but the internal accessories are more complicated. You can install all the internal accessories first. Then it is mounted on the wall by fasteners. This method is relatively simple and can be solved according to the instructions.
Different types of portable explosion proof lighting, the installation process and procedures are different, so it is quite normal to know how to install the explosion-proof lamps correctly and effectively. Now many of the purchased explosion-proof lamps have been installed in advance. It is OK to need to access the line to fix it. In fact, this method is relatively simple.
Unit battery enclosure is intended for surface mounting using the holes provided in the four mounting flanges.
1. Remove applicable hole plug(s) from top or side of enclosure for fixture/remote load attachment. AC test switch/pilot light box is intended to attach to conduit opening at bottom of unit enclosure – see figure 1.
2. Assemble fixture(s) and AC test switch/pilot light box to the unit enclosure using supplied conduit nipples, elbows, and sealing fittings where applicable – see
Fixtures, remote fused output, and AC test switch/pilot light require sealing fittings in the conduit systems within two (2) inches of the battery enclosure. Also, all conduit connections must have a minimum engagement of five (5) full threads.
3. Run appropriate wiring for fixture(s), remote load (when required), and AC test switch/pilot light to unit enclosure – see “WIRING UNIT” page 2.
4. With completion of conduit system wiring, fill sealing fittings with fiber filler and sealing cement supplied – see “SEAL INSTRUCTIONS FOR CONDUIT”, figure 3,